- SPRINKLER TALK FORUM - You Got Questions, We've Got Answers »
- Help with Design & Installation »
- Design Issues »
- water to recreational field »

Dear visitor, welcome to SPRINKLER TALK FORUM - You Got Questions, We've Got Answers. If this is your first visit here, please read the Help. It explains how this page works. You must be registered before you can use all the page's features. Please use the registration form, to register here or read more information about the registration process. If you are already registered, please login here.

Attention: The last reply to this post was 2261 days ago. The thread may already be out of date. Please consider creating a new thread.

Tuesday, May 17th 2011, 1:18pm

by jason9520

bought my 1.5" sch 40 to send water to the back. My wife said we should hold off on the additional laterals and sprinklers because f the expenses. I plan to place 4 T's on the field and run a hose off each one and run multiple (mini) raintrains in order to cut down on price. I plan to add the lateralls later. The raintrains use about 6gpm each and so I will try to run 3 which will be max gpm on my copper pipe, but running 4 at 24gpm will be awfully tempting. Materials are starting to add up, but I plan to use a backflow preventer and valves to shut off the main water supply and each of the zones. I can't wait to hook up sprinklers, but the wife must be on board or the ship will surley sink... and sprinklers won't keep a sinking ship from sinking!

Thank you HooKooDooKu for the links to the tutorial and advice.

Thank you wetboots for inspiring me to check and re-check my crazy flow numbers

Thank you Mitchgo for the "right on" advice and your links to exactly what your talking about.

You guys and others have made my rapidly confused mind more calm and confident about my lawn and watering ability. I have two young children which I hope to provide with an outlet for their energy and abilities. Your help with the water will ensure my success.

Thanks,

Jason

Thank you HooKooDooKu for the links to the tutorial and advice.

Thank you wetboots for inspiring me to check and re-check my crazy flow numbers

Thank you Mitchgo for the "right on" advice and your links to exactly what your talking about.

You guys and others have made my rapidly confused mind more calm and confident about my lawn and watering ability. I have two young children which I hope to provide with an outlet for their energy and abilities. Your help with the water will ensure my success.

Thanks,

Jason

Sunday, May 15th 2011, 12:04am

by jason9520

btw 1.5" mainline sch40pvc 250-350ft (didn't change the numbers much). and 1.0" cl200pvc for the laterals. 70-250' would all be fairly safe. 5.19ft/sec and 2.7 to 9.6 psi loss respectively

Saturday, May 14th 2011, 11:55pm

by jason9520

Great tutorial!

I checked the psi from two places off the house and both read 103psi. After figuring the losses from the backflow preventer, mainlines, valves, and 50psi for sprinklers I totaled 75psi loss.

I'm a little disappointed that the max gpm I should be taking from my 1"copper line is 18gpm.

I'm also concerned with using only 8 rainbird 8000's. I can't figure how I can get head to head coverage.

The tutorial calculated that I should run a 1.5" mainline giving me 2.8ft/sec when using 18gpm. I suppose what will keep me at 18gpm is what I choose to run off the line. In other words if I set up 4 zones running two sprinklers a zone and deciede to open two zones at a time then I could increase the gpm used but I'd be placing a strain on the pipe?

Thanks for yall's help

I checked the psi from two places off the house and both read 103psi. After figuring the losses from the backflow preventer, mainlines, valves, and 50psi for sprinklers I totaled 75psi loss.

I'm a little disappointed that the max gpm I should be taking from my 1"copper line is 18gpm.

I'm also concerned with using only 8 rainbird 8000's. I can't figure how I can get head to head coverage.

The tutorial calculated that I should run a 1.5" mainline giving me 2.8ft/sec when using 18gpm. I suppose what will keep me at 18gpm is what I choose to run off the line. In other words if I set up 4 zones running two sprinklers a zone and deciede to open two zones at a time then I could increase the gpm used but I'd be placing a strain on the pipe?

Thanks for yall's help

Wednesday, May 11th 2011, 12:51am

by Mitchgo

You can get 2 8000's shooting 50' each at 50 psi with a 1" meter at 85 psi static

Tuesday, May 10th 2011, 6:16pm

by Wet_Boots

Better to ring the field boundary with sprinkler heads, then fill in the middle of the field. The cost of water being what it is, you do better to apply it more precisely.

Tuesday, May 10th 2011, 5:33pm

by HooKooDooKu

It's a lot of reading, but if you want to begin to get an understanding of what needs to be done, then you need to read over the web site www.irrigationtutorial.com

But to get started with a few calculations, check out the charts here (specifically the page for Sch40 PVC: http://www.hunterindustries.com/resources/pdfs/technical/domestic/lit091w.pdf

One design rule is that water shouldn't travel faster than about 5fps. Based on the chart, you can see that at 10gpm, your water will flow at 6.0 fps in a 3/4" pipe, and 3.7fps in a 1" pipe. So 1" is your minimum size.

The next rule of sizing pipe is that water flowwing through a pipe loses usable water pressure. The chart will further show you that at 10gpm, you will loose 2.4psi for every 100' of pipe. Since you are talking about hundreds of feet, your pressure losses could quickly grow to about 10+ psi. Given that you are starting with 85psi, you've got some room to work with (however, other things will "steal" pressure from you as well). The chart will also show you how small increases in pipe size GREATLY reduce the pressure losses. This is because the pressure loss is a function of the square of the water speed, and water speed is a function of the square of the pipe size. So doubling pipe size cuts pressure losses by a factor of 8. So once you have a clue about all your pressure losses, you can price various pipe sizes and decide which size gives you the most bang for the buck. You're likely to find that you don't really need a 2" line, that 1-1/2" or 1-1/4 will do fine.

The next rule to consider in designing the irrigation system is how far the heads can throw water. The basic rule of thumb that Wet_Boots was giving you is that what ever is the left-over water pressure at the head in psi (after all the losses are considered from the meter, a backflow preventer, valves, and pipe) you can not expect the water to throw farther than that in feet. So if you wind up with only 30psi at the heads, you can't expect a throw with rotors of more than 30 feet. With the pipe sizes and flow you are talking about, 30psi at the heads should be very easy. Likely, once all is said and done, 40psi (and therefore 40') are reasonable expectation. But 50' of throw requires high end rotors AND a minimum of 50psi. That only gives you 15psi to lose through all the equipment listed above. That might or might not be possible. For example, if local building codes require an RPZ backflow preventer, you can expect the RPZ to steal 12-15psi all by itself.

Now practically speaking, my only irrigation experience has been designing and installing an irrigaition system myself for my home. But my best guess at this point is that you need to start by designing for 40psi at the spray heads (which means a maximum throw of 40' with rotors) and work backwards from there.

But to get started with a few calculations, check out the charts here (specifically the page for Sch40 PVC: http://www.hunterindustries.com/resources/pdfs/technical/domestic/lit091w.pdf

One design rule is that water shouldn't travel faster than about 5fps. Based on the chart, you can see that at 10gpm, your water will flow at 6.0 fps in a 3/4" pipe, and 3.7fps in a 1" pipe. So 1" is your minimum size.

The next rule of sizing pipe is that water flowwing through a pipe loses usable water pressure. The chart will further show you that at 10gpm, you will loose 2.4psi for every 100' of pipe. Since you are talking about hundreds of feet, your pressure losses could quickly grow to about 10+ psi. Given that you are starting with 85psi, you've got some room to work with (however, other things will "steal" pressure from you as well). The chart will also show you how small increases in pipe size GREATLY reduce the pressure losses. This is because the pressure loss is a function of the square of the water speed, and water speed is a function of the square of the pipe size. So doubling pipe size cuts pressure losses by a factor of 8. So once you have a clue about all your pressure losses, you can price various pipe sizes and decide which size gives you the most bang for the buck. You're likely to find that you don't really need a 2" line, that 1-1/2" or 1-1/4 will do fine.

The next rule to consider in designing the irrigation system is how far the heads can throw water. The basic rule of thumb that Wet_Boots was giving you is that what ever is the left-over water pressure at the head in psi (after all the losses are considered from the meter, a backflow preventer, valves, and pipe) you can not expect the water to throw farther than that in feet. So if you wind up with only 30psi at the heads, you can't expect a throw with rotors of more than 30 feet. With the pipe sizes and flow you are talking about, 30psi at the heads should be very easy. Likely, once all is said and done, 40psi (and therefore 40') are reasonable expectation. But 50' of throw requires high end rotors AND a minimum of 50psi. That only gives you 15psi to lose through all the equipment listed above. That might or might not be possible. For example, if local building codes require an RPZ backflow preventer, you can expect the RPZ to steal 12-15psi all by itself.

Now practically speaking, my only irrigation experience has been designing and installing an irrigaition system myself for my home. But my best guess at this point is that you need to start by designing for 40psi at the spray heads (which means a maximum throw of 40' with rotors) and work backwards from there.

Tuesday, May 10th 2011, 1:19pm

by Wet_Boots

You have to know that sprinklers do not effectively throw further, in feet of radius, than their input pressure, in psi. Simply put, you will not be getting even 50-foot throws from a one-inch meter and a static pressure of 85 psi.

Monday, May 9th 2011, 11:28pm

by jason9520

Meter is a model 70 badger 1" meter.

I tried to calculate the 2" pipe from the meter to the field and then the 1.5" pipe to 4 zones and couldn't figure out what the calculations meant. The "engineers toolkit" website spit out negative numbers even though I was considering only one zone at a time. My understanding of the gpm and psi losses are non-exsistent. I'm sure also that my zoning and sprinkler placement could be better. I think I would need approx. 50-65' of throw from these rotors in order to reach one to the other (head to head). Using the Rainbird 8005 this would be 65' with 21gpm and 50 psi. or 19gpm at 80psi. In order to run two sprinklers at a time I would need approx. 40gpm and between 50-80psi?

Do I also need double the psi, or am I wrong about all of the numbers?

Here is a scetch of my current idea of piping which includes sprinklers on the field. Please let me know how I can improve the design. I want this done right and only once as I will be doing the work myself to order to save $. I want it to seem as though I knew what I was doing you know.

Thanks again,

Jason

I tried to calculate the 2" pipe from the meter to the field and then the 1.5" pipe to 4 zones and couldn't figure out what the calculations meant. The "engineers toolkit" website spit out negative numbers even though I was considering only one zone at a time. My understanding of the gpm and psi losses are non-exsistent. I'm sure also that my zoning and sprinkler placement could be better. I think I would need approx. 50-65' of throw from these rotors in order to reach one to the other (head to head). Using the Rainbird 8005 this would be 65' with 21gpm and 50 psi. or 19gpm at 80psi. In order to run two sprinklers at a time I would need approx. 40gpm and between 50-80psi?

Do I also need double the psi, or am I wrong about all of the numbers?

Here is a scetch of my current idea of piping which includes sprinklers on the field. Please let me know how I can improve the design. I want this done right and only once as I will be doing the work myself to order to save $. I want it to seem as though I knew what I was doing you know.

Thanks again,

Jason

Monday, May 9th 2011, 8:08pm

by jason9520

In order to verify the meter and readings I used a 6gal. bucket (6gal on bottom of bucket). Turned off everything in the house and opened up a faucet from the house. The meter read 6gallons used and the bucket was all but about 1.5" from the top. Thus I'm willing to say that the meter is reading gallons and that's 4.6 seconds and 6.4 seconds for 10 gallons on the two attempts at measuring at the T valve next to the meter.

FYI the 25' hose at the end of a faucet from the houses exterior ran the 6gallons in 32.6 seconds thus approx. 11 gallons a minute.

Jason

FYI the 25' hose at the end of a faucet from the houses exterior ran the 6gallons in 32.6 seconds thus approx. 11 gallons a minute.

Jason

Monday, May 9th 2011, 4:30pm

by jason9520

Pick of meter.

I agree the numbers sound way off, bit if so I'm just figuring something wrong like the 93/98 gpm you pointed out. I'm sure I get more than 9.3 gpm though right

I agree the numbers sound way off, bit if so I'm just figuring something wrong like the 93/98 gpm you pointed out. I'm sure I get more than 9.3 gpm though right